24.301.535 APPLICATION FOR MODEL PLAN REVIEW
(1) Any manufacturer of units shall make application to the bureau for plan review of a model or model group prior to construction. The application shall include:
(a) the plan and system inspection fees as required by ARM 24.301.565;
(b) the quality control manual as outlined in ARM 24.301.536 and 24.301.543;
(c) substantiating calculations or test results indicating details of construction, plumbing, mechanical, and electrical plans when such details are required;
(d) one copy of the complete plans and specifications drawn on paper of sufficient size to provide complete details of work proposed or presented electronically in such a manner as to provide complete details of work proposed which must show:
(i) dimensioned floor plan(s);
(ii) proposed use of rooms and method of ventilation;
(iii) size, type and location of windows and exterior doors;
(iv) all necessary cross sections;
(v) floor, wall, ceiling, and roof construction details;
(vi) typical connections;
(vii) design live and dead loads;
(viii) grade and quality of materials; and
(ix) substantiating calculations or test results, where required including energy calculations as applicable.
(e) the following electrical specifications must be set forth in the plan:
(i) type and size of feeder assembly;
(ii) voltage and amperage of branch circuit panelboard;
(iii) branch circuit identification, amperage, or overcurrent protection device wire size and type;
(iv) voltage and amperage of fixed appliances;
(v) location of all appliances and fixtures;
(vi) location of all electrical outlets (receptacles and lights);
(vii) number of outlets and appliances on each circuit and circuit rating.
(f) the plan may be drawn to scale or schematic. It must set forth the following mechanical information:
(i) description of all materials, appliances, fittings, pipe, tubing, vents, and ducts;
(ii) BTUH input rating of all fuel burning appliances;
(iii) size of openings for combustion air, except where combustible air is an integral part of an approved appliance;
(iv) size, length, type, and location of vents and vent connectors;
(v) type, minimum dimension, and gauge of air ducts;
(vi) minimum free area and location of circulating air supply inlet; and
(vii) minimum free area and location of all air openings.
(g) the plan may be drawn to scale or schematic. It must set forth the following plumbing specifications:
(i) description of all materials, fixtures, fittings, pipe tubing, shower stalls, and walls;
(ii) diameter and type of pipe and tubing, and length of all trap arms;
(iii) size and type of fittings;
(iv) grade of drainage piping; and
(v) method of securing all piping.
History: 50-60-203, 50-60-401, MCA; IMP, 50-60-203, 50-60-401, 50-60-402, MCA; NEW, Eff. 3/1/75; AMD, Eff. 4/4/77; TRANS, from Dept. of Admin., Ch. 352, L. 1985, Eff. 7/1/85; AMD, 1994 MAR p. 299, Eff. 2/11/94; AMD, 1997 MAR p. 2061, Eff. 11/18/97; TRANS, from Commerce, 2001 MAR p. 2301; AMD, 2016 MAR p. 887, Eff. 5/21/16.