36.15.902 FLOODPROOFING REQUIREMENTS FOR HEATING SYSTEMS
(1) Heating systems for allowed and permitted floodplain and floodway uses shall
conform to the following conditions
(a) Float operated automatic control valves must be installed in supply lines to gas
furnaces so that the fuel supply is automatically shut off when flood waters
reach the floor level where the furnaces are located;
(b) Manually operated gate valves that can be
operated from a location above the elevation of the base flood shall also be
provided in gas supply lines; and
(c) Electric heating systems must be installed in accordance with ARM 36.15.901.
History: Sec. 76-5-208, MCA; IMP, Sec. 76-5-401 through 76-5-402, and 76-5-404 through 76-5-406, MCA; NEW, Eff. 9/4/74; AMD, 1989 MAR p. 1665, Eff. 10/27/89.